With NextGen Aire, you won’t just get expert heating and cooling results--you’ll get the whole positive customer experience package. Our experienced team accomplishes this in many ways: utilization of advanced technology, passion about serving our Newburyport, MA customers and providing readily available information about the world of HVAC, just to name a few. We’ll keep you dependably comfortable year-round with air conditioning, heating and HVAC zoning solutions.
If you’re the type of person who needs to read five-star online reviews about a heating and cooling company before making a decision, then you’re in luck! Check out our local Newburyport, MA reviews.
Matt was great, came after hours, arrived in a half an hour or less, which, considering he was a few towns away, was really quick. He was very thorough, fixed the problem and a few other things to ensure the AC system ran smoothly, and I even joined the club! Matt was very nice and quite professional.
Matthew presented us with a comprehensive solution required for our unique situation, and walked us through the entire proposal in detail during his consultation. He and his team were excellent....NGA did a great job installing our systems, and on the specific dates agreed upon. We would highly recommend NGA for home comfort solutions.
The communication throughout the process was excellent. The crew showed up on the scheduled day on time and completed the job the same day as anticipated. The quality of workmanship is excellent.
American standard air conditioning system was not cooling second floor of home. Checked system. Found thermostats calling for cooling. Zone dampers in basement working. Outdoor system running. Space load was too high for system operation time frame. Needed to run system longer. Added 2 pounds of R410-A to system. Unit running well now.
When system for second floor is running both zones. System pressures are excellent. When system drops one of he zones, the unit does not have proper air flow to remove the cooling the system produces. Installed new barometric bypass damper. Set to .3 to open when only one zone is calling. System runs well now. Customer mentioned they set thermostat to 65 @ night. Recommended only setting to minimum of 68 to prevent freezing.
Completed Installation of new Bryant high efficiency furnace installation in Beverly MA. Added air conditioning to ducted system on the first floor. Installed new Mitsubishi Ductless system on the second floor.
Customer noted issue with freeze up on AC system in Newburyport. Found system dirty. Cleaned outdoor units. Signed customer up for membership program. Customer needs some additional duct work done in attic.
Completed installation of new Bryant heat pump system in Newburyport. Replaced indoor air handler and outdoor condenser. System started up to manufacturer standards.
Setting up our new comfort advisor in our office in Newburyport! Kyle has joined our team to continue providing the best Mitsubishi ductless design in the area. He also brings a background in customer service design to help ensure we provide the most value to our customers.