Peabody, MA deserves nothing less than honest heating and air conditioning services that makes every option as clear as day, which is something NextGen Aire proudly provides.
See what Peabody, MA has to say about our top quality heating and cooling services in our customer reviews below.
Customer with high electric bill in Peabody. Checked Carrier ac system. Found the indoor system not calling for cooling however the outdoor unit was still running. Electrical in unit is welded closed. Replaced components. Tested operation. System running well. Replaced filter while on site.
Reviewed customerâ€™s Bryant heat pump system not cooling properly. Checked indoor Honeywell thermostat and made sure stat was calling correctly. Indoor unit started appropriately but the outdoor unit did not. Found the Y wire had a loose connection. Repaired wire connection. Tested operation. Unit working properly now.
Customer noted water at indoor furnace and wet filter. Checked system and found a crack in the main plate that separates the heat exchanger from the unit. Condensate leaks through this crack and down assembly to the filter.During operation, the gas valve coil is noisy which may cause failure to valve.Completed replacement of heat exchanger on furnace. During removal found 2 additional cracks in Trane furnace that was causing some poor flame patterns.Completed replacement of gas valve that was operating noisy. Checked gas line with bubble soap. Tested gas pressures. Operated system from customers thermostat.