Peabody, MA deserves nothing less than honest heating and air conditioning services that makes every option as clear as day, which is something NextGen Aire proudly provides.
See what Peabody, MA has to say about our top quality heating and cooling services in our customer reviews below.
Jeff the technician did a great job checking my central ac unit . He was very thorough and answered any questions or concerns I had .
He was great very professional and informative and explained all my options overall great experience thank you
https://www.nextgen-aire.com/filter-program Performed yearly tuneup on central air-conditioning system.
Installed air purifier and ceiling saver to central air system.
16x16x1. 20x30x1. https://www.nextgen-aire.com/filter-program
The membership on this invoice signs you up for the next year of air-conditioning maintenance. Technician has also included several estimates of work that that he recommends.
Technician inspected indoor unit with the blower fan coming on on a call for air-conditioning like it should. Technician inspected outdoor unit and noticed that blower motor was running in a reverse direction and was unable to reset the motor into the proper direction. This will cause a great deal of efficiency issues and at some point will fail. Technician also performed a refrigeration check on the unit and ascertained that it was missing approximately 2lbs of R22.No refrigeration was added to system. Technician will email estimate for repairs to customer.
Customer with high electric bill in Peabody. Checked Carrier ac system. Found the indoor system not calling for cooling however the outdoor unit was still running. Electrical in unit is welded closed. Replaced components. Tested operation. System running well. Replaced filter while on site.
Reviewed customerâ€™s Bryant heat pump system not cooling properly. Checked indoor Honeywell thermostat and made sure stat was calling correctly. Indoor unit started appropriately but the outdoor unit did not. Found the Y wire had a loose connection. Repaired wire connection. Tested operation. Unit working properly now.
Customer noted water at indoor furnace and wet filter. Checked system and found a crack in the main plate that separates the heat exchanger from the unit. Condensate leaks through this crack and down assembly to the filter. During operation, the gas valve coil is noisy which may cause failure to valve. Completed replacement of heat exchanger on furnace. During removal found 2 additional cracks in Trane furnace that was causing some poor flame patterns. Completed replacement of gas valve that was operating noisy. Checked gas line with bubble soap. Tested gas pressures. Operated system from customers thermostat.