NextGen Aire fills an HVAC industry gap in Salem, NH by providng the highest quality heating and cooling services available.
From providing diverse options to customer education, read our Salem, NH heating and cooling reviews to see how we excel as an HVAC company.
I had a few issues with my heating unit. Every time I called and had someone come out to service my unit, from the receptionist to the technicians, all where extremely polite, friendly and helpful. I had a few technicians and all where very knowledgeable. I would highly recommend NGA
Technician diagnosed faulty fan motor and blown run capacitor. Technician also noted that refrigeration charge was very low. Technician replaced fan motor and capacitor and critically charged unit.
Replaced dirty worn out flame sensor and igniter on Renni tankless hot water heater. Tested functionality multiple times and unit lit and heated water correctly. Technician noticed temperature set at 104 which is slightly lower than normal for domestic hot water. If customer notices they want more heat during showers or dishes, turning it to 120 is a standard domestic hot water temperature.
Diagnosed low refrigerant charge on Bosch heat pump unit. Performed nitrogen pressure test on unit and was able to discover small leak at suction inlet of condenser. The leak was addressed and tech vacuumed the unit down to 434 Âµm. Tech recharged the unit with 7.75 pounds of 410 a. Pressures were checked running in air-conditioning and heating. System is now back up to standard factory charge.
Installed Rinnai tankless water heater.
Replaced control board and hot surface igniter. Cycled furnace off and on via the thermostat five times with proper sequencing and ignition occurring on each relight. Also added two anchors to customers thermostat as it fell off the wall in my hand because no anchors were installed
Performed oil heating maintenance on furnace in Salem, NH. Replaced oil nozzle, filter and strainer. Performed combustion analysis and dialed system in. Furnace running very well from Ecobee thermostat.